Part of the BACHARACH family of products. HGM / RDM Refrigerant Gas. Monitoring System. Refrigerant Gas Detection,. Identification & Monitoring. Refrigerant monitoring system • Read online or download PDF • Bacharach HGM User Manual. View and Download Bacharach HGM installation, operation & maintenance instructions manual online. Refrigerant Gas Monitoring System. HGM
|Published (Last):||27 May 2016|
|PDF File Size:||12.81 Mb|
|ePub File Size:||3.50 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dirt, grease, and oils can adversely affect the operation of the HGM This enables the HGM to be setup from a personal computer. Once the blockage bgm300 been cleared, the HGM will return to normal operation after the zone has been sampled.
Ensure the source voltage matches the voltage of the product before energizing the equipment.
This manual also for: Page 84 It is strongly recommended that any New Gas curves that are added be done in conjunction with help from Bacharach, Inc. Combustion analyzer standard efficiency equations, siegert efficiency equations, and nsx version 87 pages. The prominent features of the display module are discussed below. Page 64 Clearing System Faults If the fault condition is associated with an HGM, the monitor will return to normal operation soon after the problem is corrected.
Location This is the name you assign to the HGM to identify its location. It may have up to 12 alphanumeric characters. If you are unfamiliar with complex systems of this type, it is recommended that you contact Bacharach for technical assistance.
Bacharach HGM300 Installation, Operation & Maintenance Instructions Manual
To place a zone on hold, press and hold down the key adjacent to that zone until you hear a beep. There are two versions of PC software. Check for a blockage in the air sample line or at the line end filter.
The default is 60 minutes. Once the HGM completes a measurement cycle in the affected zone the alarm condition will be indicated.
Clearing System Faults If the fault condition is associated with an HGM, the monitor will return to normal operation soon after the problem is corrected. An exhaust line is installed to vent residual gas away from the monitor. After a brief moment the System Screen is displayed.
Bacharach HGM User Manual | 26 pages
RDM Mounting Specs Installation Hold the display module flat against the mounting surface and allow it to slide down engaging the screw All pending alarms across the entire network must be acknowledged bacharafh the RDM returns to normal operation. Service Pursuant to the stated warranty, Bacharach, Inc.
ggm300 The monitor should be installed out of direct sunlight in a clean, dry area that is not subject to temperature or humidity extremes. Page of 94 Go.
Bacharach HGM Halogen Gas Monitor | LEL International
Fault Log Register Register 0x, 0xh bytes These registers contain the 20 most recent fault events, bachatach time they occurred, and a pointer to the most recent event. Hgm – Electrical Wiring Locate service knockouts on exterior of enclosure and install electrical conduit in the typical manner.
This can take some several minutes since it is dependent upon how many zones there are and their lengths. Distance This is the tubing length in feet from the HGM to the termination of the air intake line. Repeat this procedure to acknowledge any remaining alarms.
Press the adjacent key to adjust the value.
Page 67 Programming New Gasses As new refrigerants come into use the HGM allows the addition of these new gases to its on-board refrigerant gas library. This document will assume that the reader is familiar with the various parameters used to setup the HGM, as well as the different operational modes that the HGM may be placed in. If more than one HGM is connected to the network, it will sequentially poll each monitor for its status.
Basic hgm300/rdm800 monitor system connection – Bacharach HGM300 User Manual
Parameters must also be defined for each HGM monitor connected to the network. This value may range from 0 to feet. Programming New Gasses As new refrigerants come into use the HGM allows the addition of these new gases to its on-board refrigerant gas library.
DO NOT use soap and water. Use any of the remaining service knockouts to gain access to the interior of the monitor.